AUTOMATIC HOT WATER BOILER
The boiler ROJEK A 15 is designed for heating buildings with low heat loss, adjustable power 3 – 14 kW.
Automatic hot water boiler A 15 enables to burn wooden pellets 6 – 8 mm diam. – both high quality white pellets and pellets of lower quality with bark mixture in automatic operation.
Retort burner enables to burn also lower quality bio fuels – plant pellets and in combination with an adapter also corn.
|Nominal output||14 kW|
|Min. output||3 kW|
|Boiler width||507 mm|
|Boiler height||1105 mm|
|Boiler depth||780 mm|
|Boiler depth, incl. chimney||780 mm|
|Chimney height||625 mm|
|Chimney diameter||129 mm|
|Height of water inlet||133 mm|
|Diameter of water inlet and outlet||2″|
|Boiler weight||310 kg|
|Boiler class in accordance with Norm EN 303-5||5|
|Energy efficiency class of wood / coal||A + / –|
|Energy Efficiency Index (EEI) of pellets / coal||112 / –|
|Seasonal energy efficiency of pellets / coal||77 % / –|
|Boiler emissions according to Commission Regulation (EU) No. 2015/1189||EKODESIGN|
|Hydraulic boiler loss||59 mbar|
|Water volume||106 l|
|Max. operation water overpressure||2 bar|
|Min. operation water overpressure||0,5 bar|
|Testing water overpressure||4 bar|
|Max. operation temperature||90 °C|
|Specified chimney draught||10 – 15 Pa|
|Consumption of wooden pellets with nominal power||2,9 kg/h|
|Consumption of wooden pellets for minimum capacity||0,9 kg/h|
|Temperature of burnt gas for nominal output||180 °C|
|Hopper volume 300l|
|Hopper volume||300 l|
|Approx. weight of pellets in hopper||180 kg|
|Boiler width, incl. hopper||1 130 mm|
guarantee for the tightness of boiler body 3 years
In automatic operation the boiler complies with Class 5 – EKODESIGN in accordance with the norm EN 303-5.
Thanks to the fuel tank, electronic regulation and the burner with spiral feeder the boiler can work in automatic operation even for several days. The electronic regulation can be connected with a circular pump ( adjustment of temperature when the pump switches on ) and at the same time with room thermostat.
The controller basically contains a built-in module for controlling a four-way or three-way mixing valve. Furthermore, the ST 480 zPID controller can cooperate with an equithermal sensor, with other four-way or three-way valves, with a room thermostat, with a GSM module, with an Ethernet module (via the Internet)
The burner is installed in the lower part of boiler body. The retort burner is designed for lower fuel loading and the combustion process itself can be compared with a blacksmith hearth. From the tank the fuel is feeded by spiral feeder to the retort knee. Here it is forced out up to a round grate.
Both the grate and the retort are made of high quality cast iron. The retort is placed in a converter to which the air is blown by a blower. Through the slots between the retort and the grate the air is then driven to the burning fuel layer.